Publication UMA-EN-P – November Table of Contents . User Manual UM to assign an IP address to the MicroLogix. controller. Publication INC-EN-P – October Important . Manual UM .. publication UM, for more information on surge suppression. rm_-en-p – Free ebook download as PDF File .pdf), Text File .txt) or read book online for free. Document Number IN UM
|Published (Last):||25 January 2010|
|PDF File Size:||13.35 Mb|
|ePub File Size:||15.61 Mb|
|Price:||Free* [*Free Regsitration Required]|
Locate your controller as far as possible from power lines, load lines, and other sources of electrical noise such as hard-contact switches, relays, and ac motor drives. Finger-safe cover TIP If you wire the terminal block with the finger-safe cover removed, you may not be able to put it back on the terminal block if the wires are in the way.
Uk001 sections of this publication may contain additional information regarding specific enclosure jm001 ratings that are required to comply um0001 certain product safety certifications. Drill holes through the template. Follow these steps to connect the replaceable battery. Store the equipment in appropriate static-safe packaging when not in use. Make sure your controller is spaced properly see Controller Spacing on page 12 for more information.
IN – Rockwell Automation
When the battery is low, the indicator is set displayed as a solid rectangle. For AC-powered controllers, this connection must be made for safety purposes. AC powered products must be connected to the secondary of an isolating transformer.
DIN rail mounting dimensions are shown below. Debris strip ATTENTION Do not km001 the protective debris strip until after the controller and all other equipment in the panel near km001 controller are mounted and wiring is complete.
For more eh on proper grounding guidelines, see the Industrial Automation Wiring and Grounding Guidelines, publication Use AWG 14 wire. For more information on proper grounding guidelines, refer to the Industrial Automation Wiring and Grounding Guidelines, publication Communication pins used for RS communications are alternately used for 24V power on the other MicroLogix controllers.
Because of this difference, and also because of the wide variety of uses for solid state equipment, all persons responsible for applying this equipment must satisfy themselves that each intended application of this equipment is acceptable. Outside United 176 Please contact your local Rockwell Automation representative for the return procedure. Power Loss in Transmission Lines. Additional noise immunity can be obtained by routing the cables in grounded conduit.
The drain wire and foil shield must be grounded at one end of the cable. You must also provide an acceptable grounding path for each device in your application. Make sure that the MicroLogix system is properly grounded. Tighten the terminal screw, making sure the pressure plate secures the wire. If it is open, close the DIN latch.
Mount your DIN rail. Use a power supply that matches the transmitter specifications as shown.
Scripting must be enabled to use this site.
Wear an approved grounding wriststrap. Throughout this manual, when necessary, we use notes to make you aware of safety considerations. The Belden cable has two signal wires black and clearone drain wire, and a foil shield. Each product is supplied with markings on the rating nameplate indicating the hazardous location temperature code. Because of the many variables and requirements associated with any particular installation, Rockwell Automation, Inc. Trademarks not belonging to Rockwell Automation are property of their respective companies.
Several specific steps can be taken to help reduce the effects of environmental noise on analog signals: When combining products within a system, the most adverse temperature code lowest “T” number may be used to help determine the overall temperature code of the system.
Remove the mounting template from inside the back cover of this document. Plug the ribbon cable connector into the bus connector. However, because of the variety of applications and environments where analog controllers are installed and operated, it is impossible to ensure that all environmental noise will be removed by the input filters. Be sure that power is removed or the area is nonhazardous before proceeding.
This could cause an explosion in hazardous location installations.
New Product Satisfaction Return Rockwell Un001 tests all of its products to ensure that they are fully operational when shipped from the manufacturing facility. Installation Assistance If you experience a problem within the first 24 hours of installation, please review the information that’s contained in this manual. Documents Flashcards Grammar checker.
Um0001 not touch circuit components inside the equipment. Once wiring is complete, remove protective debris strip. When using spade lugs, use a small, flat-blade screwdriver to pry the finger-safe cover from the terminal blocks, then loosen the terminal screw. Make sure that the placement of the controller on the DIN rail meets the recommended spacing requirements see Controller Spacing on page 12 for more information.
Output group to output group isolation Verified by one of the following dielectric tests: Output 2, 3 and 4 may be used like the other FET transistor outputs, but em addition, within a limited current range, they may be operated at a higher speed. At this level transient voltages are controlled and do not exceed the impulse voltage capability of the product’s insulation. However, if your product is not functioning and needs to be returned, follow these procedures.
The examples and diagrams in this manual are included um01 for illustrative purposes.